// CODE SNIPPET
1112.10 Pressure-Relief Device Settings
JUMP TO FULL CODE CHAPTER
Rupture members used in lieu of, or in series with, a relief valve shall have a nominal rated rupture pressure not exceeding the design pressure of the parts of the system protected. The conditions of application shall comply with ASME BPVC Section VIII. The size of rupture members installed ahead of relief valves shall not be less than the relief-valve inlet. [ASHRAE 15:9.5.2]
Related Code Sections
1112.10 Refrigeration, Pressure-Relief Device Settings
Pressure-relief valves shall start to function at a pressure not exceeding the design pressure of the parts of the system protected. Exception ...
2018 Uniform Mechanical Code of Nevada > 11 Refrigeration > 1112.0 Pressure-Relief Devices > 1112.10 Pressure-Relief Device Settings
1111.2 Refrigeration, Setting
by a highside pressure relief device, the compressor's pressure limiting device shall be set not more than 90 percent of the operating pressure ...
2018 Uniform Mechanical Code of Nevada > 11 Refrigeration > 1111.0 Pressure-Limiting Devices > 1111.2 Setting
M2301.2.3 Solar Thermal Energy Systems, Pressure and Temperature Relief Valves and System Components
System components containing fluids shall be protected with temperature and pressure relief valves or pressure relief valves. Relief devices shall ...
Residential Code 2018 of Nevada > 23 Solar Thermal Energy Systems > M2301 Solar Thermal Energy Systems > M2301.2 Design and Installation > M2301.2.3 Pressure and Temperature Relief Valves and System Components
1116.1.1 Refrigeration, Testing Procedure
pressure-relief device shall be set above the test pressure but low enough to prevent permanent deformation of the system's components. Exceptions ...
2018 Uniform Mechanical Code of Nevada > 11 Refrigeration > 1116.0 Testing of Refrigeration Equipment > 1116.1 Factory Tests > 1116.1.1 Testing Procedure