// CODE SNIPPET
1117.1.1 Pressure-Relief Device
JUMP TO FULL CODE CHAPTER
Related Code Sections
1112.0 Refrigeration, Pressure-Relief Devices
Refrigeration systems shall be protected by a pressure-relief device or other approved means to safely relieve pressure due to fire or abnormal ...
1117.1.1 Refrigeration, Pressure-Relief Device
Where a pressure-relief device is used to protect a pressure vessel having an inside dimension of 6 inches (152 mm) or less, the ultimate strength ...
2018 Uniform Mechanical Code of Nevada > 11 Refrigeration > 1117.0 Refrigerant-Containing Pressure Vessels > 1117.1 Inside Dimensions 6 Inches or Less > 1117.1.1 Pressure-Relief Device
1113.4 Refrigeration, Parallel Pressure-Relief Devices
Two or more pressure-relief devices in parallel to obtain the required capacity shall be considered as one pressure-relief device. The discharge ...
2018 Uniform Mechanical Code of Nevada > 11 Refrigeration > 1113.0 Overpressure Protection > 1113.4 Parallel Pressure-Relief Devices
1115.4 Refrigeration, Marking of Pressure-Relief Devices
Pressure-relief valves for refrigerant-containing components shall be set and sealed by the manufacturer or an assembler in accordance with ASME BPVC ...
2018 Uniform Mechanical Code of Nevada > 11 Refrigeration > 1115.0 Labeling and Identification > 1115.4 Marking of Pressure-Relief Devices
1112.11.2 Refrigeration, Discharging Location Exterior to Building
Pressure-relief devices designed to discharge external to the refrigeration system shall be arranged to discharge outside of a building and shall ...
2018 Uniform Mechanical Code of Nevada > 11 Refrigeration > 1112.0 Pressure-Relief Devices > 1112.11 Discharge From Pressure-Relief Devices > 1112.11.2 Discharging Location Exterior to Building