// CODE SNIPPET
P-812.1 Pressure Relief
JUMP TO FULL CODE CHAPTER
An approved pressure relief valve shall be installed on all equipment used for heating or storing hot water and which forms part of a water supply system. The rate of discharge of such valve shall limit the pressure rise in the water supply system to 10% above the pressure at which the valve is set to open. Pressure relief valves shall be of the spring-loaded type with a pull rod and lever handle, or shall be of an equivalent approved type which will permit the manual operation and testing of the valve. Pressure relief valves shall be installed in the cold water supply to the heater or storage tank and adjacent to such heater or storage tank. In addition, an approved backflow preventer shall be installed on all equipment which is connected to the potable water supply when such equipment is used for any purpose other than supplying potable water to approved fixtures or as required by the Department.
Related Code Sections
P-812.1 Water Supply and Distribution, Pressure Relief
An approved pressure relief valve shall be installed on all equipment used for heating or storing hot water and which forms part of a water supply ...
Philadelphia Plumbing Code > 8 Water Supply and Distribution > P-812 Temperature and Pressure Relief Valves > P-812.1 Pressure Relief
1006.3 Boilers, Water Heaters and Pressure Vessels, Pressure Relief for Pressure Vessels
Pressure vessels shall be protected with a pressure relief valve or pressure-limiting device as required by the manufacturer's installation ...
2018 Philadelphia Mechanical Code > 10 Boilers, Water Heaters and Pressure Vessels > 1006 Safety and Pressure Relief Valves and Controls > 1006.3 Pressure Relief for Pressure Vessels
5303.3 Compressed Gases, Pressure Relief Devices
Pressure relief devices shall be in accordance with Sections 5303.3.1 through 5303.3.5 ...
2018 Philadelphia Fire Code > 53 Compressed Gases > 5303 General Requirements > 5303.3 Pressure Relief Devices
5503.2 Cryogenic Fluids, Pressure Relief Devices
Pressure relief devices shall be provided in accordance with Sections 5503.2.1 through 5503.2.7 to protect containers and systems containing ...
2018 Philadelphia Fire Code > 55 Cryogenic Fluids > 5503 General Requirements > 5503.2 Pressure Relief Devices
606.5.10 Water Supply and Distribution, Pressure Relief for Tanks
Every pressure tank in a hydropneumatic pressure booster system shall be protected with a pressure relief valve. The pressure relief valve shall ...
Plumbing Code 2018 of Philadelphia > 6 Water Supply and Distribution > 606 Installation of the Building Water Distribution System > 606.5 Water Pressure Booster Systems > 606.5.10 Pressure Relief for Tanks