C408.2.4 Preliminary Commissioning Report
A preliminary report of commissioning test procedures and results shall be completed and certified by the registered design professional or approved agency and provided to the building owner. The report shall be identified as "Preliminary Commissioning Report" and shall identify:
- Itemization of deficiencies found during testing required by this section that have not been corrected at the time of report preparation.
- Deferred tests that cannot be performed at the time of report preparation because of climatic conditions.
- Climatic conditions required for performance of the deferred tests.
Buildings, or portions thereof, shall not pass the final mechanical inspection until such time as the code official has received a letter of transmittal from the building owner acknowledging that the building owner has received the Preliminary Commissioning Report.
The code official shall be permitted to require that a copy of the Preliminary Commissioning Report be made available for review by the code official.