// CODE SNIPPET
188.8.131.52* Power-Generation Buildings
JUMP TO FULL CODE CHAPTER
Buildings of noncombustible construction used exclusively for the enclosure of steam generators, steam turbines, gas turbines, heat recovery generators, and flue gas treatment equipment shall be permitted to have a maximum travel distance of 400 ft (122 m), where all special hazards are protected by approved automatic suppression systems in accordance with one or more of the following standards, as applicable:
- NFPA 11, Standard for Low-, Medium-, and High-Expansion Foam
- NFPA 12, Standard on Carbon Dioxide Extinguishing Systems
- NFPA 13, Standard for the Installation of Sprinkler Systems
- NFPA 15, Standard for Water Spray Fixed Systems for Fire Protection
- NFPA 16, Standard for the Installation of Foam-Water Sprinkler and Foam-Water Spray Systems
- NFPA 17, Standard for Dry Chemical Extinguishing Systems
- NFPA 750, Standard on Water Mist Fire Protection Systems
- NFPA 2001, Standard on Clean Agent Fire Extinguishing Systems
Related Code Sections
184.108.40.206* Industrial Occupancies, Power-Generation Buildings
Buildings of noncombustible construction used exclusively for the enclosure of steam generators, steam turbines, gas turbines, heat recovery ...
Life Safety Code 2018 of Kansas > 40 Industrial Occupancies > 40.2 Means of Egress Requirements > 40.2.6 Travel Distance to Exits > 220.127.116.11* Power-Generation Buildings
(A) Special Conditions, General Requirements
the time required for the application. The supply system for critical operations power, in addition to the normal services to the building and meeting ...
National Electrical Code 2017 of Kansas > 7 Special Conditions > 708 Critical Operations Power Systems (COPS) > 708.20 Sources of Power > (A) General Requirements
220.12 Wiring and Protection, Lighting Load for Specified Occupancies
regarding the total general lighting load of the building. The power monitoring system will be set with alarm values to alert the building owner or manager ...
National Electrical Code 2017 of Kansas > 2 Wiring and Protection > 220 Branch-Circuit, Feeder, and Service Load Calculations > 220.12 Lighting Load for Specified Occupancies
691.4 Special Equipment, Special Requirements for Large-Scale PV Electric Supply Stations
the PV electric supply station shall only be used to power auxiliary equipment for the generation of the PV power. Large-scale PV electric supply ...
National Electrical Code 2017 of Kansas > 6 Special Equipment > 691 Large-Scale Photovoltaic (PV) Electric Power Production Facility > 691.4 Special Requirements for Large-Scale PV Electric Supply Stations
Section R107 Scope and Administration, Temporary Structures and Uses
and general welfare. The building official ...