// CODE SNIPPET
804.2 Post-Construction, Pre-Occupancy Baseline IAQ Testing
JUMP TO FULL CODE CHAPTER
Where this section is indicated to be applicable in Table 302.1, and after all interior finishes are installed, the building shall be tested for indoor air quality and the testing results shall indicate that the levels of VOCs meet the levels detailed in Table 804.2 using testing protocols in accordance with ASTM D 6196, ASTM D 5466, ASTM D 5197, ASTM D 6345, and ISO 7708. Test samples shall be taken in not less than one location in each 25,000 square feet (1860 m2) of floor area or in each contiguous floor area.
- Group F, H, S and U occupancies shall not be required to comply with this section.
- A building shall not be required to be tested where a similarly designed and constructed building as determined by the code official, for the same owner or tenant, has been tested for indoor air quality and the testing results indicate that the level of VOCs meet the levels detailed in Table 804.2.
- Where the building indoor environment does not meet the concentration limits in Table 804.2 and the tenant does not address the air quality issue by mitigation and retesting, the building shall be flushed-out by supplying continuous ventilation with all air-handling units at their maximum outdoor air rate for at least 14 days while maintaining an internal temperature of at least 60°F (15.6°C), and relative humidity not higher than 60 percent. Occupancy shall be permitted to start 7 days after start of the flush-out, provided that the flush-out continues for the full 14 days.
|MAXIMUM CONCENTRATION OF AIR
POLLUTANTS RELEVANT TO IAQ
ug/m3 (unless otherwise noted)
|t-Butyl methyl ether||8000|
|Carbon monoxide||9 ppm and no greater than 2
ppm above outdoor levels
|Particulates (PM 2.5)||35 (24-hr)|
|Particulates (PM 10)||150 (24-hr)|
|Total volatile organic compounds (TVOC)||500|
- This chemical has a limit only where carpets and fabrics with styrene butadiene rubber (SBR) latex backing material are installed as part of the base building systems.
Related Code Sections
804.2 Indoor Environmental Quality and Comfort, Post-Construction, Pre-Occupancy Baseline IAQ Testing
to comply with this section. A building shall not be required to be tested where a similarly designed and constructed building as determined by the code ...
Green Construction Code 2012 of Maryland > 8 Indoor Environmental Quality and Comfort > 804 Specific Indoor Air Quality and Pollutant Control Measures > 804.2 Post-Construction, Pre-Occupancy Baseline IAQ Testing
Section 302 Jurisdictional Requirements and Life Cycle Assessment, Jurisdictional Requirements
702.7 Municipal reclaimed water Yes No CHAPTER 8. INDOOR ENVIRONMENTAL QUALITY AND COMFORT 804.2 Post-Construction Pre-Occupancy ...
Green Construction Code 2012 of Maryland > 3 Jurisdictional Requirements and Life Cycle Assessment > 302 Jurisdictional Requirements
Section 901 Commissioning, Operation and Maintenance, General
The provisions of this chapter are intended to facilitate the pre- and post-occupancy commissioning, operation and maintenance of buildings ...
903.1 Commissioning, Operation and Maintenance, General
and material qualities. TABLE 903.1 COMMISSIONING PLAN CONSTRUCTION OR SYSTEM REQUIRING VERIFICATION PREOCCUPANCY POST- OCCUPANCY ...
Green Construction Code 2012 of Maryland > 9 Commissioning, Operation and Maintenance > 903 Commissioning > 903.1 General
1004.3 Means of Egress, Posting of Occupant Load
Every room or space that is an assembly occupancy shall have the occupant load of the room or space posted in a conspicuous place, near the main ...
Building Code 2015 of Maryland > 10 Means of Egress > 1004 Occupant Load > 1004.3 Posting of Occupant Load