// CODE SNIPPET
313.6 Portable Natural Gas Heaters
JUMP TO FULL CODE CHAPTER
Heaters shall be located outdoors and at least 5 feet (1524 mm) from any building or structure.
Heaters shall not be located beneath, or closer than 5 feet (1524 mm) to combustible decorations and combustible overhangs, awnings, sun control devices or similar combustible attachments to buildings or structures.
Heaters shall be equipped with a tilt or tip-over switch that automatically shuts off the flow of gas if the appliance is tilted more than 15 degrees (0.26 rad) from the vertical.
The heating element or combustion chamber of heaters shall be permanently protected so as to prevent accidental contact by persons or material.