// CODE SNIPPET
5706.6.4 Portable Fire Extinguisher
JUMP TO FULL CODE CHAPTER
During unloading of the tank vehicle, the portable fire extinguisher shall be out of the carrying device on the vehicle and shall be 15 feet (4572 mm) or more from the unloading valves.
Related Code Sections
Section 1105 Aviation Facilities, Portable Fire Extinguishers
Portable fire extinguishers suitable for flammable or combustible liquid and electrical-type fires shall be provided as specified in Sections 1105.2 ...
1208.4 Dry Cleaning, Portable Fire Extinguishers
Portable fire extinguishers shall be selected, installed and maintained in accordance with this section and Section 906. A minimum of two 2-A:10-B:C ...
Section 1415 Fire Safety During Construction and Demolition, Portable Fire Extinguishers
Structures under construction, alteration or demolition shall be provided with not less than one approved portable fire extinguisher in accordance ...
2010 Fire Code of NY > 14 Fire Safety During Construction and Demolition > 1415 Portable Fire Extinguishers
1505.4.2 Flammable Finishes, Portable Fire Extinguishers
Areas in the vicinity of dip tanks shall be provided with portable fire extinguishers complying with Section 906 and suitable for flammable ...
2010 Fire Code of NY > 15 Flammable Finishes > 1505 Dipping Operations > 1505.4 Fire Protection > 1505.4.2 Portable Fire Extinguishers
2003.5 Manufacture of Organic Coatings, Portable Fire Extinguishers
A minimum of one portable fire extinguisher complying with Section 906 for extra hazard shall be provided in organic coating areas ...
2010 Fire Code of NY > 20 Manufacture of Organic Coatings > 2003 General Precautions > 2003.5 Portable Fire Extinguishers