// CODE SNIPPET
(C) Pool Water
JUMP TO FULL CODE CHAPTER
Where none of the bonded parts are in direct connection with the pool water, the pool water shall be in direct contact with an approved corrosion-resistant conductive surface that exposes not less than 5800 mm2 (9 in.2) of surface area to the pool water at all times. The conductive surface shall be located where it is not exposed to physical damage or dislodgement during usual pool activities, and it shall be bonded in accordance with 680.26(B).
Related Code Sections
(C) Special Equipment, Pool Water
Where none of the bonded parts are in direct connection with the pool water, the pool water shall be in direct contact with an approved corrosion ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 680 Swimming Pools, Fountains, and Similar Installations > 680.26 Equipotential Bonding > (C) Pool Water