// CODE SNIPPET
(A) Point of Supply
Related Code Sections
(A) Special Conditions, Point of Supply
Overcurrent devices shall be located at the point where the conductor to be protected receives its supply ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 725 Class 1, Class 2, and Class 3 Remote- Control, Signaling, and Power-Limited Circuits > 725.45 Class 1 Circuit Overcurrent Device Location > (A) Point of Supply
(1) Equipment for General Use, Loads at Transformer Supply Points Only
Where all loads are connected at the transformer supply points at each end of the tie and overcurrent protection is not provided in accordance ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 450 Transformers and Transformer Vaults (Including Secondary Ties) > 450.6 Secondary Ties > (A) Tie Circuits > (1) Loads at Transformer Supply Points Only
408.6 Equipment for General Use, Short-Circuit Current Rating
-and two-family dwelling units, the available fault current and the date the calculation was performed shall be field marked on the enclosure at the point ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 408 Switchboards, Switchgear, and Panelboards > 408.6 Short-Circuit Current Rating
(A) Wiring and Protection, Location
point of the supply transformer or generator ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 250 Grounding and Bonding > 250.187 Impedance Grounded Systems > (A) Location
(D) Special Occupancies, Patient Care Vicinity Grounding and Bonding (Optional)
A patient care vicinity shall be permitted to have a patient equipment grounding point. The patient equipment grounding point, where supplied, shall ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 517 Health Care Facilities > 517.19 Category 1 (Critical Care) Spaces > (D) Patient Care Vicinity Grounding and Bonding (Optional)