// CODE SNIPPET
P-1102.3 Plastic Pipes
JUMP TO FULL CODE CHAPTER
Vent pipes of ABS plastic and PVC plastic shall be limited to installations of buildings containing dwelling units only. Such buildings shall consist of from one to four families and shall not exceed three stories in height. For the purpose of this section, basements are not considered a story height.
PVC joints shall be solvent weld.
Related Code Sections
404.17 Gas Piping Installations, Plastic Pipe
The installation of plastic pipe shall comply with Sections 404.17.1 through 404.17.3 ...
2018 Philadelphia Fuel Gas Code > 4 Gas Piping Installations > 404 (IFGC) Piping System Installation > 404.17 Plastic Pipe
405.3 Gas Piping Installations, Plastic Pipe
Plastic pipe bends shall comply with the following: The pipe shall not be damaged and the internal diameter of the pipe shall not be effectively ...
2018 Philadelphia Fuel Gas Code > 4 Gas Piping Installations > 405 (IFGS) Piping Bends and Changes in Direction > 405.3 Plastic Pipe
503.4.1 Chimneys and Vents, Plastic Piping
Where plastic piping is used to vent an appliance, the appliance shall be listed for use with such venting materials and the appliance manufacturer's ...
2018 Philadelphia Fuel Gas Code > 5 Chimneys and Vents > 503 (IFGS) Venting of Appliances > 503.4 Type of Venting System to Be Used > 503.4.1 Plastic Piping
P-1005.5 Storm Water Drainage Piping, Plastic Pipe
ABS plastic and PVC plastic pipe and fittings authorized by Sections P-1005.1 and P-1005.3 shall be installed in accordance with Section P-305.0 ...
Philadelphia Plumbing Code > 10 Storm Water Drainage Piping > P-1005 Materials > P-1005.5 Plastic Pipe