// CODE SNIPPET
Section G2418 (407) Piping Support
JUMP TO FULL CODE CHAPTER
Piping shall be supported with metal pipe hooks, metal pipe straps, metal bands, metal brackets, metal hangers or building structural components suitable for the size of piping, of adequate strength and quality, and located at intervals so as to prevent or damp out excessive vibration. Piping shall be anchored to prevent undue strains on connected appliances and shall not be supported by other piping. Pipe hangers and supports shall conform to the requirements of MSS SP-58 and shall be spaced in accordance with Section G2424. Supports, hangers and anchors shall be installed so as not to interfere with the free expansion and contraction of the piping between anchors. The components of the supporting equipment shall be designed and installed so that they will not be disengaged by movement of the supported piping.
Related Code Sections
Section G2418 Fuel Gas, (407) Piping Support
Piping shall be provided with support in accordance with Section G2418.2 ...
Section 407 Gas Piping Installations, (IFGC) Piping Support
Piping shall be provided with support in accordance with Section 407.2 ...
Section 407 Fixtures, Faucets and Fixture Fittings, Bathtubs
The outlets shall be connected to waste tubing or piping not less than 1 1 / 2 inches (38 mm) in diameter. The waste outlet shall be equipped ...
Section 407 Special Detailed Requirements Based on Occupancy and Use, Group I-2
with Section 1002.2 shall identify the building components necessary to support a defend-in-place emergency response in accordance with Sections 403 and 404 ...
Building Code 2018 of Kansas > 4 Special Detailed Requirements Based on Occupancy and Use > 407 Group I-2