// CODE SNIPPET
G.5 Piping Requirements
JUMP TO FULL CODE CHAPTER
High pressure gas piping shall comply with the requirements of this section.
Installations of natural gas piping operating at pressures of 125 psig (862 kPa gauge) and above shall comply with the requirements of ASME B 31.1.
Horizontal piping that traverses within a building from a protected room or shaft to a protected room or shaft shall be run in an outer pipe of the same pressure rating as the inner pipe. The outer pipe shall be welded and the annular space between the inner and outer pipe shall be equal to or greater than the inside diameter of the inner pipe. The annular space shall be monitored for natural gas with an approved gas detection alarm system and shall be vented to the exterior of the building. The outer pipe must open to the shaft and/or protected room or to the outside air.
An emergency gas shutoff valve shall be provided on the gas supply outside of any room containing an appliance utilizing gas at a pressure at or above 15 psig (103 kPa gauge). The emergency shutoff valve shall be controlled from a break glass station located outside the room served and from the gas detection system monitoring the room. The emergency shutoff valve shall automatically stop the gas flow to the room(s) containing the appliance(s) in the event of an unsafe condition. The emergency shutoff valve shall be manually operable. Emergency gas shutoff valve bypasses shall be prohibited.
Related Code Sections
G.5 High Pressure Natural Gas Installations, Piping Requirements
High pressure gas piping shall comply with the requirements of this section ...
406.7.1 Gas Piping Installations, Piping Systems Required to Be Purged Outdoors
The purging of piping systems shall be in accordance with the provisions of Sections 406.7.1.1 through 406.7.1.4 where the piping system meets either ...
NYC Fuel Gas Code 2014 > 4 Gas Piping Installations > 406 Inspection, Testing and Purging > 406.7 Purging > 406.7.1 Piping Systems Required to Be Purged Outdoors
504.6 Water Heaters, Requirements for Discharge Piping
The discharge piping serving a pressure relief valve, temperature relief valve or combination thereof shall: Not be directly connected ...
NYC Plumbing Code 2014 > 5 Water Heaters > 504 Safety Devices > 504.6 Requirements for Discharge Piping
406.7 Gas Piping Installations, Purging
accumulation of flammable mixtures. The remaining gas in this section of pipe shall be displaced with an inert gas as required by Table 406.7.1 ...
NYC Fuel Gas Code 2008 > 4 Gas Piping Installations > 406 Inspection, Testing and Purging > 406.7 Purging
406.7.2 Gas Piping Installations, Placing in Operation
Where piping full of air is placed in operation, the air in the piping shall be displaced with fuel gas, except where such piping is required ...
NYC Fuel Gas Code 2008 > 4 Gas Piping Installations > 406 Inspection, Testing and Purging > 406.7 Purging > 406.7.2 Placing in Operation