// CODE SNIPPET
Article 10 Piping Containing Steam, Hot Water or Other Fluids
JUMP TO FULL CODE CHAPTER
All accessible piping in habitable and occupiable rooms carrying steam, water, or other fluids at temperatures exceeding one hundred sixty-five degrees Fahrenheit shall be insulated to prevent the temperature at the outer surface of the insulation from exceeding sixty degrees Fahrenheit above the ambient temperature. The openings for insulated piping through combustible floors, walls, partitions, ceilings and other combustible construction shall include clearance and insulation adequate to satisfy the requirements of section 27-792 of article one of this subchapter. Where accessible piping carries a fluid not exceeding two hundred fifty degrees Fahrenheit and insulation would interfere with the functioning of the system, such piping may be uninsulated provided sufficient clearance is maintained from the combustible construction so that the temperature limitation of section 27-792 of article one of this subchapter is not exceeded, and all uninsulated piping shall be provided with at least one-half inch clearance from combustible materials.
For requirements governing firestopping around piping passing through floors, roofs, or fire separations, see subchapter five of this chapter.
All insulations shall be of noncombustible materials. All coverings, vapor barriers and adhesives shall have a flame spread rating no higher than twenty-five and a smoke developed rating no higher than fifty. Adhesives and mastic finishes shall be tested in sufficient bulk to produce maximum burning, and shall be tested in accordance with reference standard RS 14-11.
Related Code Sections
Article 10 Heating and Combustion Equipment, Piping Containing Steam, Hot Water or Other Fluids
All accessible piping in habitable and occupiable rooms carrying steam, water, or other fluids at temperatures exceeding one hundred sixty-five ...
NYC 1968 Code (Vol I) > 14 Heating and Combustion Equipment > 10 Piping Containing Steam, Hot Water or Other Fluids
Reference Standard 16 Plumbing and Gas Piping [PDF] (page 63)
Reference Standard 16 ASPIRATOR.-A fitting or device that is supplied with water or other fluid under positive pressure. The water or other fluid ...
1210.3 Hydronic Piping, Existing Systems
Existing steam piping systems shall be in accordance with Sections 1210.3.1 through 1210.3.3. Upon the completion of a new high-pressure steam piping ...
NYC Mechanical Code 2014 > 12 Hydronic Piping > 1210 High-Pressure Steam and High Temperature Hot Water Piping Systems > 1210.3 Existing Systems
Section 1201 Hydronic Piping, General
apply to hydronic piping systems that are part of heating, ventilation and air-conditioning systems. Such piping systems shall include steam, hot water ...