// CODE SNIPPET
Related Code Sections
603.1.2 Types of Construction, Piping
The use of combustible piping materials shall be permitted where installed in accordance with the limitations of the International Mechanical Code ...
Building Code 2018 of Illinois > 6 Types of Construction > 603 Combustible Material in Types I and II Construction > 603.1 Allowable Materials > 603.1.2 Piping
2308.5.8 Wood, Pipes in Walls
Stud partitions containing plumbing, heating or other pipes shall be framed and the joists underneath spaced to provide proper clearance ...
Building Code 2018 of Illinois > 23 Wood > 2308 Conventional Light-Frame Construction > 2308.5 Wall Construction > 2308.5.8 Pipes in Walls
(B) Wiring and Protection, Pipe Organs
Generator and motor frames in an electrically operated pipe organ, unless effectively insulated from ground and the motor driving it ...
National Electrical Code 2017 of Illinois > 2 Wiring and Protection > 250 Grounding and Bonding > 250.112 Specific Equipment Fastened in Place (Fixed) or Connected by Permanent Wiring Methods > (B) Pipe Organs
415.11.6 Special Detailed Requirements Based on Occupancy and Use, Piping and Tubing
Hazardous production materials piping and tubing shall comply with this section and ASME B31.3 ...
Building Code 2018 of Illinois > 4 Special Detailed Requirements Based on Occupancy and Use > 415 Groups H-1, H-2, H-3, H-4 and H-5 > 415.11 Group H-5 > 415.11.6 Piping and Tubing
417.2 Special Detailed Requirements Based on Occupancy and Use, Piping Clearance
Overhead heating pipes shall have a clearance of not less than 2 inches (51 mm) from combustible contents in the dryer ...
Building Code 2018 of Illinois > 4 Special Detailed Requirements Based on Occupancy and Use > 417 Drying Rooms > 417.2 Piping Clearance