// CODE SNIPPET
609.11.2 Pipe Insulation Wall Thickness
JUMP TO FULL CODE CHAPTER
Hot water pipe insulation shall have a minimum wall thickness of not less than the diameter of the pipe for a pipe up to 2 inches (50 mm) in diameter. Insulation wall thickness shall be not less than 2 inches (51 mm) for a pipe of 2 inches (50 mm) or more in diameter.
Related Code Sections
609.11.2 Water Supply and Distribution, Pipe Insulation Wall Thickness
Hot water pipe insulation shall have a minimum wall thickness of not less than the diameter of the pipe for a pipe up to 2 inches (50 mm) in diameter ...
2018 Uniform Plumbing Code of Nevada > 6 Water Supply and Distribution > 609.0 Installation, Testing, Unions, and Location > 609.11 Pipe Insulation > 609.11.2 Pipe Insulation Wall Thickness
L 501.2 Sustainable Practices, Insulation
Hot water supply and return piping shall be thermally insulated. The wall thickness of the insulation shall be equal to the nominal diameter ...
2018 Uniform Plumbing Code of Nevada > L Sustainable Practices > L 501.0 Water Heating Design, Equipment, and Installation > L 501.2 Insulation
L 503.3.3 Sustainable Practices, Insulation
:7.4.3] TABLE L 503.3.3 MINIMUM PIPING INSULATION THICKNESS FOR HEATING AND HOT-WATER SYSTEMS (STEAM, STEAM CONDENSATE, HOT-WATER HEATING, AND ...
2018 Uniform Plumbing Code of Nevada > L Sustainable Practices > L 503.0 Service Hot Water — Other Than Low-Rise Residential Buildings > L 503.3 Mandatory Provisions > L 503.3.3 Insulation
C403.2.8 [CE] Commercial Energy Efficiency, Piping Insulation
) TABLE C403.2.8 MINIMUM PIPE INSULATION THICKNESS (thickness in inches) a FLUID OPERATING TEMPERATURE RANGE AND USAGE ( ° F ...
Energy Conservation Code 2012 of Nevada > 4 [CE] Commercial Energy Efficiency > C403 Building Mechanical Systems > C403.2 Provisions Applicable to All Mechanical Systems (Mandatory) > C403.2.8 Piping Insulation
E 502.5 Sustainable Practices, Insulation for Piping
] TABLE E 502.5 MINIMUM PIPE INSULATION THICKNESS 1, 5 [ASHRAE 90.2:TABLE 6.5] INSULATION CONDUCTIVITY NOMINAL PIPE DIAMETER (inches ...
2018 Uniform Mechanical Code of Nevada > E Sustainable Practices > E 502.0 Heating, Ventilation, and Air-Conditioning Low-Rise Residential Buildings > E 502.5 Insulation for Piping