// CODE SNIPPET
1109.7 Pipe Enclosure
JUMP TO FULL CODE CHAPTER
Refrigerant piping and tubing shall be installed so that it is not subject to damage from an external source. Soft annealed copper tubing shall not exceed 13/8 inches (35 mm) nominal size. Mechanical joints, other than approved press-connect joints, shall not be made on tubing exceeding 3/4 of an inch (20 mm) nominal size. Soft annealed copper tubing conveying refrigerant shall be enclosed in iron or steel piping and fittings, or in conduit, molding, or raceway that will protect the tubing against mechanical injury from an exterior source.
- Tubing entirely within or tubing within 5 feet (1524 mm) of a refrigerant compressor where so located that it is not subject to external injury.
- Copper tubing serving a dwelling unit, where such tubing contains Group A1 refrigerant and is placed in locations not subject to damage from an external source.
Related Code Sections
1109.7 Refrigeration, Pipe Enclosure
Refrigerant piping and tubing shall be installed so that it is not subject to damage from an external source. Soft annealed copper tubing shall ...
2018 Uniform Mechanical Code of Nevada > 11 Refrigeration > 1109.0 Refrigeration Piping, Containers, and Valves > 1109.7 Pipe Enclosure
650.9 Special Equipment, Protection From Accidental Contact
The wiring of the sounding apparatus shall be within the lockable enclosure (organ chamber) where the exterior pipes shall be permitted to form part ...
National Electrical Code 2017 of Nevada > 6 Special Equipment > 650 Pipe Organs > 650.9 Protection From Accidental Contact
1310.6 Health Care Facilities and Medical Gas and Medical Vacuum Systems, Backfilling and Trenching
conduit, cover, or enclosure shall be self-draining and not retain groundwater in prolonged contact with the pipe. [NFPA 99:126.96.36.199.5.3 ...
2018 Uniform Plumbing Code of Nevada > 13 Health Care Facilities and Medical Gas and Medical Vacuum Systems > 1310.0 Installation of Piping > 1310.6 Backfilling and Trenching
188.8.131.52 System Requirements, Supply
The supply for the sprinkler in the dry pipe valve enclosure shall be either from the dry side of the system or from a wet pipe sprinkler system ...
Standard for the Installation of Sprinkler Systems 2016 of Nevada > 7 System Requirements > 7.2* Dry Pipe Systems > 7.2.5* Location and Protection of Dry Pipe Valve > 184.108.40.206 Supply
908.3.3 Fire Protection Systems, Valve Closure
downstream of a piping distribution manifold, the shutoff valve in the gas valve enclosure for the branch line located in the piping distribution ...
Building Code 2012 of Nevada > 9 Fire Protection Systems > 908 Emergency Alarm Systems > 908.3 Highly Toxic and Toxic Materials > 908.3.3 Valve Closure