// CODE SNIPPET
1026.11 Photoluminescent Exit Path Marking
JUMP TO FULL CODE CHAPTER
Photoluminescent exit path markings in high-rise buildings subject to Section 403.16 shall be provided in accordance with this section. All exit path markings required herein shall be of an approved photoluminescent material. The markings shall be washable, non-toxic, non radioactive, and if subjected to fire must be self extinguishing when the flame is removed. Exit path markings shall at a minimum be located:
1. On all doors opening to exits, exit passageways, or horizontal exits and shall be marked with the word "EXIT".
Exception: Within street level lobbies where egress direction is immediately discernable.
Related Code Sections
1026.11 Means of Egress, Photoluminescent Exit Path Marking
Photoluminescent exit path markings in high-rise buildings subject to Section 403.16 shall be provided in accordance with this section. All exit path ...
NYC Building Code 2008 > 10 Means of Egress > 1026 Signage > 1026.11 Photoluminescent Exit Path Marking
1704.30 Structural Tests and Special Inspections, Photoluminescent Exit Path Markings
The installation of photoluminescent egress path markings shall be subject to special inspection. The special inspector shall verify that approved ...
NYC Building Code 2014 > 17 Structural Tests and Special Inspections > 1704 Special Inspections > 1704.30 Photoluminescent Exit Path Markings
403.16 Special Detailed Requirements Based on Use and Occupancy, Exit Path Markings
All high-rise buildings shall be provided with photoluminescent exit path markings conforming to Section 1026. Exception: Exit ...
NYC Building Code 2008 > 4 Special Detailed Requirements Based on Use and Occupancy > 403 High-Rise Buildings > 403.16 Exit Path Markings
1006.3.2 Means of Egress, Performance of System
-to-minimum illumination uniformity ratio of 40 to 1 shall not be exceeded. In buildings that contain existing photoluminescent exit path markings tested ...
NYC Building Code 2014 > 10 Means of Egress > 1006 Means of Egress Illumination > 1006.3 Illumination Emergency Power > 1006.3.2 Performance of System
Reference Standard 6 Means of Egress [PDF] (page 1)
Reference Standard 6 REFERENCE STANDARD RS-6 MEANS OF EGRESS † REFERENCE STANDARD RS 6-1 PHOTOLUMINESCENT EXIT PATH MARKINGS as required by Local ...