// CODE SNIPPET
(C) Phase-Fault Protection
Related Code Sections
(C) Equipment for General Use, Phase-Fault Protection
Phase-fault protection shall be provided in each phase, consisting of a separate phase-overcurrent relay connected to a separate current transformer ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 490 Equipment Over 1000 Volts, Nominal > 490.72 Branch-Circuit Requirements > (C) Phase-Fault Protection
(E) Special Conditions, Ground-Fault Protection
-to-phase, ground-fault protection meeting the requirements of 230.95, shall be provided ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 705 Interconnected Electric Power Production Sources > 705.11 Supply-Side Source Connections > (E) Ground-Fault Protection
(A) Special Equipment, Outlets
Outlets supplied by branch circuits not exceeding 150 volts to ground and 60 amperes, single-phase, shall be provided with ground-fault circuit ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 682 Natural and Artificially Made Bodies of Water > 682.15 Ground-Fault Protection > (A) Outlets
680.71 Special Equipment, Protection
ground-fault circuit interrupter. All 125-volt, single-phase receptacles not exceeding 30 amperes and located within 1.83 m (6 ft) measured horizontally ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 680 Swimming Pools, Fountains, and Similar Installations > 680.71 Protection
210.13 Wiring and Protection, Ground-Fault Protection of Equipment
, but not exceeding 600 volts phase-to-phase, shall be provided with ground-fault protection of equipment in accordance with 230.95. Informational Note: For ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 210 Branch Circuits > 210.13 Ground-Fault Protection of Equipment