// CODE SNIPPET
508.3.3 Permanent Lighting
JUMP TO FULL CODE CHAPTER
Permanent lighting shall be provided at the roof access. The switch for such lighting shall be located inside the building near the access means leading to the roof. [NFPA 54:22.214.171.124]
Related Code Sections
508.3.3 Water Heaters, Permanent Lighting
Permanent lighting shall be provided at the roof access. The switch for such lighting shall be located inside the building near the access means ...
2021 Oregon Plumbing Specialty Code > 5 Water Heaters > 508.0 Appliances on Roofs > 508.3 Appliances on Roofs > 508.3.3 Permanent Lighting
N1104.1 [RE] Energy Efficiency, (R404.1) Lighting Equipment (Mandatory)
Not less than 90 percent of the permanently installed lighting fixtures shall contain only high-efficacy lamps ...
2021 Oregon Residential Specialty Code (ORSC) > 11 [RE] Energy Efficiency > N1104 (R404) Electrical Power and Lighting Systems (Mandatory) > N1104.1 (R404.1) Lighting Equipment (Mandatory)
(A) Equipment for General Use, Lighting Track
Lighting track shall be permanently installed and permanently connected to a branch circuit. Only lighting track fittings shall be installed ...
2021 Oregon Electrical Specialty Code (OESC) > 4 Equipment for General Use > 410 Luminaires, Lampholders, and Lamps > 410.151 Installation > (A) Lighting Track
9.4.3 Lighting, Dwelling Units
Not less than 75% of the permanently installed lighting fixtures shall use lamps with an efficacy of at least 55 lm/W or have a total ...
2021 Oregon Energy Efficiency Specialty Code (OEESC) > 9 Lighting > 9.4 Mandatory Provisions > 9.4.3 Dwelling Units
520.74 Special Occupancies, Pilot Lights Required
to indicate when the circuit is energized. Each pilot light shall be permanently identified indicating a description of the circuit controlled. Pilot lights ...
2021 Oregon Electrical Specialty Code (OESC) > 5 Special Occupancies > 520 Theaters, Audience Areas of Motion Picture and Television Studios, Performance Areas, and Similar Locations > 520.74 Pilot Lights Required