tee or other approved
connection shall be inserted horizontally beneath the sheeting and connected to a 3- or 4-inch-diameter
(76 or 102 mm) fitting with a vertical vent
pipe installed through the sheeting. The vent
pipe shall be extended up through the building floors, and terminate at least 12 inches (305 mm) above the roof in a location at least 10 feet (3048 mm) away from any window or other opening into the conditioned spaces
of the building that is less than 2 feet (610 mm) below the exhaust point, and 10 feet (3048 mm) from any window or other opening in adjoining or adjacent buildings.