// CODE SNIPPET
E3706.3 Panelboard Overcurrent Protection
JUMP TO FULL CODE CHAPTER
In addition to the requirement of Section E3706.1, a panelboard shall be protected by an overcurrent protective device having a rating not greater than that of the panelboard. Such overcurrent protective device shall be located within or at any point on the supply side of the panelboard. (408.36)
Related Code Sections
E3706.3 Branch Circuit and Feeder Requirements, Panelboard Overcurrent Protection
In addition to the requirement of Section E3706.1, a panelboard shall be protected by an overcurrent protective device having a rating not greater ...
Residential Code 2018 of Kansas > 37 Branch Circuit and Feeder Requirements > E3706 Panelboards > E3706.3 Panelboard Overcurrent Protection
(A) Special Equipment, Panelboards and Overcurrent Protection
Use of standard single-phase panelboards and distribution equipment with a higher voltage rating shall be permitted. The system shall be clearly ...
National Electrical Code 2017 of Kansas > 6 Special Equipment > 647 Sensitive Electronic Equipment > 647.4 Wiring Methods > (A) Panelboards and Overcurrent Protection
(B) Equipment for General Use, Supplied Through a Transformer
Where a panelboard is supplied through a transformer, the overcurrent protection required by 408.36 shall be located on the secondary side ...
National Electrical Code 2017 of Kansas > 4 Equipment for General Use > 408 Switchboards, Switchgear, and Panelboards > 408.36 Overcurrent Protection > (B) Supplied Through a Transformer
E3405.5 General Requirements, Location of Working Spaces and Equipment
Required working space shall not be designated for storage. Panelboards and overcurrent protection devices shall not be located in clothes closets ...
Residential Code 2018 of Kansas > 34 General Requirements > E3405 Equipment Location and Clearances > E3405.5 Location of Working Spaces and Equipment
(1) Wiring and Protection, Taps Not Over 3 m (10 ft) Long
of the overcurrent device protecting the feeder conductors. Informational Note: For overcurrent protection requirements for panelboards, see 408.36 ...
National Electrical Code 2017 of Kansas > 2 Wiring and Protection > 240 Overcurrent Protection > 240.21 Location in Circuit > (B) Feeder Taps > (1) Taps Not Over 3 m (10 ft) Long