// CODE SNIPPET
P-808.6 Overflow for Water Supply Tanks
JUMP TO FULL CODE CHAPTER
Overflow outlets for gravity tanks shall not be less than 4 inches below the tank supply and shall discharge at least 6 inches above a roof or within 6 inches of a floor drain or they shall discharge over and above the flood level rim of an open water supplied sink or other approved receptacle having a trap with a diameter equal to that of the overflow pipe.
Overflow pipes shall be properly screened against the entrance of insects or vermin.
Overflow outlets shall terminate in a horizontal position above a roof or in a turned-down position above a sink or receptacle.
Overflows shall be sized as specified in Table P-808.
|Tank Capacity (Gallons)||Minimum Size Drain Pipe (Inches)||Minimum Size Overflows|
|Up to 750||1-1/4||One size larger than supply pipe|
|75 to 1500||1-1/2|
|1501 to 3000||2|
|3001 to 5000||2-1/2|
|5001 to 7500||3||One size larger than supply pipe
(Minimum size 4")
Related Code Sections
P-808.6 Water Supply and Distribution, Overflow for Water Supply Tanks
as specified in Table P-808. TABLE P-808 — WATER SUPPLY TANK DRAINS AND OVERFLOWS Tank Capacity (Gallons) Minimum Size Drain ...
Philadelphia Plumbing Code > 8 Water Supply and Distribution > P-808 Water Supply Tanks > P-808.6 Overflow for Water Supply Tanks
606.5.4 Water Supply and Distribution, Overflows for Water Supply Tanks
A gravity or suction water supply tank shall be provided with an overflow with a diameter not less than that shown in Table 606.5.4. The overflow ...
Plumbing Code 2018 of Philadelphia > 6 Water Supply and Distribution > 606 Installation of the Building Water Distribution System > 606.5 Water Pressure Booster Systems > 606.5.4 Overflows for Water Supply Tanks
P2712.5 Plumbing Fixtures, Overflows in Flush Tanks
Flush tanks shall be provided with overflows discharging to the water closet connected thereto and such overflow shall be of sufficient size ...
Philadelphia Residential Code > 27 Plumbing Fixtures > P2712 Water Closets > P2712.5 Overflows in Flush Tanks
P2910.9.5 Water Supply and Distribution, Makeup Water
of makeup water for the storage tank. The makeup water supply shall be protected against backflow by means of an air gap not less than 4 inches (102 mm ...
Philadelphia Residential Code > 29 Water Supply and Distribution > P2910 Nonpotable Water Systems > P2910.9 Nonpotable Water Storage Tanks > P2910.9.5 Makeup Water