// CODE SNIPPET
E3705.5 Overcurrent Protection Required
JUMP TO FULL CODE CHAPTER
All ungrounded branch-circuit and feeder conductors shall be protected against overcurrent by an overcurrent device installed at the point where the conductors receive their supply. Overcurrent devices shall not be connected in series with a grounded conductor. Overcurrent protection and allowable loads for branch circuits and for feeders that do not supply the entire load associated with a one-family dwelling or the entire load associated with an individual dwelling unit in a two-family dwelling shall be in accordance with this chapter.
Branch-circuit conductors and equipment shall be protected by overcurrent protective devices having a rating or setting not exceeding the allowable ampacity specified in Table E3705.1 and Sections E3705.2, E3705.3 and E3705.4 except where otherwise permitted or required in Sections E3705.5.1 through E3705.5.3. [240.4, 240.21, and 310.15(B)(7)(2)]
The next higher standard overcurrent device rating, above the ampacity of the conductors being protected, shall be permitted to be used, provided that all of the following conditions are met:
- The conductors being protected are not part of a branch circuit supplying more than one receptacle for cord- and plug-connected portable loads.
- The ampacity of conductors does not correspond with the standard ampere rating of a fuse or a circuit breaker without overload trip adjustments above its rating (but that shall be permitted to have other trip or rating adjustments).
- The next higher standard device rating does not exceed 400 amperes. [240.4(B)]
Except as specifically permitted by Section E3705.5.4, the rating of overcurrent protection devices shall not exceed the ratings shown in Table E3705.5.3 for the conductors specified therein. [240.4(D)]
TABLE E3705.5.3 [240.4(D)]
|COPPER||ALUMINUM OR COPPER-CLAD |
|Maximum overcurrent- |
|Maximum overcurrent |
Related Code Sections
E3705.5 Branch Circuit and Feeder Requirements, Overcurrent Protection Required
All ungrounded branch-circuit and feeder conductors shall be protected against overcurrent by an overcurrent device installed at the point where ...
Residential Code 2018 of Kansas > 37 Branch Circuit and Feeder Requirements > E3705 Conductor Sizing and Overcurrent Protection > E3705.5 Overcurrent Protection Required
215.1 Wiring and Protection, Scope
This article covers the installation requirements, overcurrent protection requirements, minimum size, and ampacity of conductors for feeders ...
(B) Equipment for General Use, Supplied Through a Transformer
Where a panelboard is supplied through a transformer, the overcurrent protection required by 408.36 shall be located on the secondary side ...
National Electrical Code 2017 of Kansas > 4 Equipment for General Use > 408 Switchboards, Switchgear, and Panelboards > 408.36 Overcurrent Protection > (B) Supplied Through a Transformer
(D) Wiring Methods and Materials, Overcurrent Protection
Tap connections from conductors in auxiliary gutters shall be provided with overcurrent protection as required in 240.21 ...
National Electrical Code 2017 of Kansas > 3 Wiring Methods and Materials > 366 Auxiliary Gutters > 366.56 Splices and Taps > (D) Overcurrent Protection
(B) Wiring and Protection, Feeder Taps
Conductors tapped to a feeder shall be permitted to be protected by the feeder overcurrent device where that overcurrent device also protects the tap ...
National Electrical Code 2017 of Kansas > 2 Wiring and Protection > 240 Overcurrent Protection > 240.101 Additional Requirements for Feeders > (B) Feeder Taps