// CODE SNIPPET
66.15 Outdoor Storage
JUMP TO FULL CODE CHAPTER
This section shall apply to the storage of liquids outdoors in the following:
- Drums or other containers that do not exceed 119 gal (450 L) individual capacity
- Portable tanks that do not exceed 660 gal (2500 L) individual capacity
- Intermediate bulk containers that do not exceed 793 gal (3000 L) individual capacity
Outdoor storage of liquids in containers, intermediate bulk containers, and portable tanks shall comply with Table 66.15.3 and with all applicable requirements of this section. [30:15.3]
|Liquid Class||Containers||Portable Tanks and Metal IBCs||Rigid Plastic and Composite IBCs||Minimum Separation Distance (ft)|
|Maximum Quantity per Pile (gal)a,b,c||Maximum Storage Height (ft)||Maximum Quantity per Pile (gal)||Maximum Storage Height (ft)||Maximum Quantity per Pile (gal)a,c||Maximum Storage Height (ft)||Between Piles or Rack Sections||To Property Line That Is or Can Be Built Uponb,d||To Street, Alley, or Public Wayb|
For SI units, 1 ft = 0.3 m; 1 gal = 3.8 L.
NP: Not permitted.
bSee 18.104.22.168 for smaller pile sizes.
cFor storage in racks, the quantity limits per pile do not apply, but the rack arrangements should be limited to a maximum of 50 ft (15 m) in length and two rows or 9 ft (2.7 m) in depth.
Where total quantity stored does not exceed 50 percent of the maximum quantity per pile, as specified in Table 66.15.3, the distances to a property line that is or can be built upon and to streets, alleys, or public ways shall be permitted to be reduced by 50 percent but in no case to less than 3 ft (0.9 m). [30:15.3.4]
The storage area shall be graded in a manner to divert possible spills away from buildings or other exposures or shall be surrounded by a curb at least 6 in. (150 mm) high. [30:15.3.5]
When accessible to the public, the storage area shall be protected against tampering and trespassing. [30:15.3.6]
A maximum of 1100 gal (4160 L) of liquids in containers, intermediate bulk containers, or portable tanks shall be permitted to be stored adjacent to a building under the same management, provided the following conditions apply:
- The adjacent building wall has an exterior fire resistance rating of 2 hours.
- The adjacent building wall has no openings at grade or above grade that are within 10 ft (3 m) horizontally of the storage.
- The adjacent building wall has no openings directly above the storage.
- The adjacent building wall has no openings below grade within 50 ft (15 m) horizontally of the storage.
The quantity of liquid stored adjacent to a building that meets the conditions of 22.214.171.124(1) through (4) shall be permitted to exceed that permitted in 126.96.36.199, provided the maximum quantity per pile does not exceed 1100 gal (4160 L) and each pile is separated by a 10 ft (3 m) minimum clear space along the common wall. [30:15.4.3]
The quantity of liquid stored shall be permitted to exceed the 1100 gal (4160 L) quantity specified by 188.8.131.52 where a minimum distance equal to that specified by Table 66.15.3 for distance to property line shall be maintained between buildings and the nearest container or portable tank. [30:15.4.4]
Related Code Sections
34.10.3* General Storage, Outdoor Storage
The storage of wood and wood composite pallets or listed pallets equivalent to wood at pallet manufacturing and pallet recycling facility sites shall ...
Fire Code 2018 of West Virginia > 34 General Storage > 34.10 Storage of Idle Pallets > 34.10.3* Outdoor Storage
184.108.40.206 Compressed Gases and Cryogenic Fluids, Outdoor Storage
Cryogenic fluids in stationary or portable containers stored outdoors shall be in accordance with 220.127.116.11. [ 55: 18.104.22.168 ...
Fire Code 2018 of West Virginia > 63 Compressed Gases and Cryogenic Fluids > 63.4 Cryogenic Fluids > 63.4.13 Storage > 22.214.171.124 Outdoor Storage
66.15 Flammable and Combustible Liquids, Outdoor Storage
This section shall apply to the storage of liquids outdoors in the following: Drums or other containers that do not exceed 119 gal (450 L ...
66.9.19 Flammable and Combustible Liquids, Outdoor Storage of Liquids
Storage of liquids outside of buildings shall meet the requirements of Section 66.14 or 66.15, whichever is applicable. [ 30: 9.19] ...
Fire Code 2018 of West Virginia > 66 Flammable and Combustible Liquids > 66.9 Storage of Liquids in Containers — General Requirements > 66.9.19 Outdoor Storage of Liquids
414.6 Special Detailed Requirements Based on Use and Occupancy, Outdoor Storage, Dispensing and Use
The outdoor storage, dispensing and use of hazardous materials shall be in accordance with the NFPA Life Safety Code 2018 edition ...
Building Code 2015 of West Virginia > 4 Special Detailed Requirements Based on Use and Occupancy > 414 Hazardous Materials > 414.6 Outdoor Storage, Dispensing and Use