// CODE SNIPPET
5704.2.13.1.2 Out of Service for 90 Days
JUMP TO FULL CODE CHAPTER
- Flammable or combustible liquids shall be removed from the tank.
- All piping, including fill line, gauge opening, vapor return and pump connection, shall be capped or plugged and secured from tampering.
- Vent lines shall remain open and be maintained in accordance with Sections 5704.2.7.3 and 5704.2.7.4.