// CODE SNIPPET
1910.106(h)(6)(ii) Other Controls
JUMP TO FULL CODE CHAPTER
Where the special hazards of operation or exposure indicate a need, the following fire control provision shall be provided.
A reliable water supply shall be available in pressure and quantity adequate to meet the probable fire demands.
Hydrants shall be provided in accordance with accepted good practice.
Hose connected to a source of water shall be installed so that all vessels, pumps, and other equipment containing flammable liquids can be reached with at least one hose stream. Nozzles that are capable of discharging a water spray shall be provided.
Processing plants shall be protected by an approved automatic sprinkler system or equivalent extinguishing system. If special extinguishing systems including but not limited to those employing foam, carbon dioxide, or dry chemical are provided, approved equipment shall be used and installed in an approved manner.