// CODE SNIPPET
(B) Other Circuits
JUMP TO FULL CODE CHAPTER
Any areas of ITE that require servicing of parts that are greater than 30 volts rms, 42 volts peak, or 60 volts dc shall comply with the workspace requirements of 646.19.
Informational Note No. 1: For example, field-wiring compartments for ac mains connections, power distribution units, and so forth.
Informational Note No. 2: It is assumed that ITE operates at voltages not exceeding 1000 volts.