// CODE SNIPPET
(B) Other Cables
JUMP TO FULL CODE CHAPTER
Cables that are not approved for mounting in contact with a building or other structure shall be mounted on insulating supports installed at intervals not exceeding 4.5 m (15 ft) and in a manner that maintains a clearance of not less than 50 mm (2 in.) from the surface over which they pass.
Related Code Sections
(B) Wiring and Protection, Other Cables
Cables that are not approved for mounting in contact with a building or other structure shall be mounted on insulating supports installed ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 230 Services > 230.51 Mounting Supports > (B) Other Cables
(3) Wiring Methods and Materials, Other Nonshielded Cables
Other nonshielded cables not covered in 300.50(A)(1) or (A)(2) shall be installed in rigid metal conduit, intermediate metal conduit, or rigid ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 300 General Requirements for Wiring Methods and Materials > 300.50 Underground Installations > (A) General > (3) Other Nonshielded Cables
(E) Special Conditions, Class 2 or Class 3 Cables With Other Circuit Cables
Jacketed cables of Class 2 or Class 3 circuits shall be permitted in the same enclosure, cable tray, raceway, or cable routing assembly with jacketed ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 725 Class 1, Class 2, and Class 3 Remote- Control, Signaling, and Power-Limited Circuits > 725.139 Installation of Conductors of Different Circuits in the Same Cable, Enclosure, Cable Tray, Raceway, or Cable Routing Assembly > (E) Class 2 or Class 3 Cables With Other Circuit Cables
727.5 Special Conditions, Uses Not Permitted
Type ITC cable shall not be installed on circuits operating at more than 150 volts or more than 5 amperes. Installation of Type ITC cable with other ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 727 Instrumentation Tray Cable: Type ITC > 727.5 Uses Not Permitted
(1) Special Equipment, Cables
Cable shall be listed Type AC cable or listed Type MC cable containing nominal 600-volt, 8 to 12 AWG insulated copper conductors. Other cables ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 604 Manufactured Wiring Systems > 604.100 Construction > (A) Cable or Conduit Types > (1) Cables