// CODE SNIPPET
118.104.22.168 Other Battery Technologies
JUMP TO FULL CODE CHAPTER
- Gas detection systems complying with Section 916 shall be provided in accordance with Section 122.214.171.124 where the batteries have the potential to produce toxic or highly toxic gas in the storage room or cabinet in excess of the permissible exposure limits (PEL) during charging, discharging and normal system operation.
- Mechanical ventilation shall be provided in accordance with Section 1126.96.36.199.
- Spill control and neutralization shall be in accordance with Section 1188.8.131.52.
- In addition to the signage required in Section 1184.108.40.206, the marking shall identify the type of batteries present, describe the potential hazards associated with the battery type, and indicate that the room contains energized electrical circuits.