1616A.1.40 Operational Nonstructural Performance Level Requirements
Exception: A new building which is required for general acute care services that is added to an existing general acute care hospital and which has a building area of 4,000 square feet (371 m2) or less, need not satisfy the NPC-5 requirements until the deadline specified in California Administrative Code (Part 1, Title 24 CCR), Chapter 6.
Hospitals and buildings designed and constructed to the provisions of this code for new construction shall be deemed to satisfy Operational Nonstructural Performance Level (NPC-5) requirements when:
- The facility has on-site supplies of water and holding tanks for sewage and liquid waste, sufficient to support 72 hours of emergency operations for the hospital or building, which are integrated into the building plumbing systems in accordance with the California Plumbing Code.
- An on-site emergency system as defined in the California Electrical Code is incorporated into the building electrical system for critical care areas. Additionally, the system shall provide for radiological service and an onsite fuel supply for 72 hours of acute care operation.
Emergency and standby generators shall not be located below the higher of the Design Flood Elevation (DFE) or Base Flood Elevation (BFE) plus two feet (BFE + 2 ft.) or 500 year flood elevation, whichever is higher, and shall be located at an elevation close to grade for easy accessibility from outside for maintenance.