// CODE SNIPPET
[F] 703.8 Opening Protective Closers
JUMP TO FULL CODE CHAPTER
Where openings are required to be protected, opening protectives shall be maintained self-closing or automatic-closing by smoke detection. Existing fusible-link-type automatic door-closing devices shall be replaced if the fusible link rating exceeds 135°F (57°C).
Related Code Sections
703.8 Fire Safety Requirements, Opening Protective Closers
Where openings are required to be protected, opening protectives shall be maintained self-closing or automatic-closing by smoke detection. Existing ...
Property Maintenance Code 2018 of South Holland > 7 Fire Safety Requirements > 703 Fire-Resistance Ratings > 703.8 Opening Protective Closers
703.2 Fire-Resistance-Rated Construction, Opening Protectives
Opening protectives shall be maintained in an operative condition in accordance with NFPA 80. Where allowed by the fire code official ...
Fire Code 2012 of South Holland > 7 Fire-Resistance-Rated Construction > 703 Fire-Resistance-Rated Construction > 703.2 Opening Protectives
718.104.22.168 Fire and Smoke Protection Features, Delayed-Action Closers
Doors required to be self-closing and not required to be automatic closing shall be permitted to be equipped with delayed-action closers ...
Building Code 2018 of South Holland > 7 Fire and Smoke Protection Features > 716 Opening Protectives > 716.2 Fire Door Assemblies > 716.2.6 Fire Door Hardware and Closures > 722.214.171.124 Delayed-Action Closers
705.2.3 Fire and Smoke Protection Features, Hold-Open Devices and Closers
Hold-open devices and automatic door closers, where provided, shall be maintained. During the period that such device is out of service for repairs ...
Fire Code 2018 of South Holland > 7 Fire and Smoke Protection Features > 705 Door and Window Openings > 705.2 Inspection and Maintenance > 705.2.3 Hold-Open Devices and Closers
909.20.2.1 Fire Protection Systems, Door Closers
Doors in a smokeproof enclosure shall be self- or automatic closing by actuation of a smoke detector in accordance with Section 7126.96.36.199 and shall ...
Building Code 2012 of South Holland > 9 Fire Protection Systems > 909 Smoke Control Systems > 909.20 Smokeproof Enclosures > 909.20.2 Construction > 909.20.2.1 Door Closers