// CODE SNIPPET
E 402.2 Open-Ended Gastight Conduit
JUMP TO FULL CODE CHAPTER
The open-ended gastight conduit shall conform to the requirements in the following:
- The conduit shall be not less than Schedule 40 pipe that is approved for underground installation beneath buildings.
- The interior diameter of the conduit shall be not less than 1/2 of an inch (15 mm) larger than the outside diameter of the gas piping.
- The conduit shall extend to a point not less than 4 inches (102 mm) beyond the outside wall of the manufactured home or accessory building or structure, and the outer ends shall not be sealed.
- Where the conduit terminates within a manufactured home or accessory building or structure, it shall be accessible, and the space between the conduit and the gas piping shall be sealed to prevent leakage of gas into the building. [NFPA 501A:126.96.36.199 — 188.8.131.52.4]