// CODE SNIPPET
711.2.1 Omission of Vents for Horizontal Stack Offsets
JUMP TO FULL CODE CHAPTER
Vents for horizontal stack offsets required by Section 711.2 shall not be required where the stack and its offset are one pipe size larger than required for a building drain [see Table 710.1(1)] and the entire stack and offset are not less in cross-sectional area than that required for a straight stack plus the area of an offset vent as provided for in Section 907.
Related Code Sections
711.2.1 Sanitary Drainage, Omission of Vents for Horizontal Stack Offsets
Vents for horizontal stack offsets required by Section 711.2 shall not be required where the stack and its offset are one pipe size larger than ...
Plumbing Code 2018 of Kansas > 7 Sanitary Drainage > 711 Offsets in Drainage Piping in Buildings of Five Stories or More > 711.2 Horizontal Stack Offsets > 711.2.1 Omission of Vents for Horizontal Stack Offsets
917.7 Vents, Stack Offsets
Where fixture drains are not connected below a horizontal offset in a stack , a horizontal offset shall not be required to be vented. Where ...
Section 907 Vents, Vents for Stack Offsets
Horizontal offsets of drainage stacks shall be vented where five or more branch intervals are located above the offset. The offset shall ...
913.2 Vents, Stack Installation
The waste stack shall be vertical, and both horizontal and vertical offsets shall be prohibited between the lowest fixture drain connection ...