// CODE SNIPPET
Section 1306 Oil Gauging
JUMP TO FULL CODE CHAPTER
Tanks in which a constant oil level is not maintained by an automatic pump shall be equipped with a method of determining the oil level.
Test wells shall not be installed inside buildings. For outdoor service, test wells shall be equipped with a tight metal cover designed to discourage tampering.
Gauging devices such as liquid level indicators or signals shall be designed and installed so that oil vapor will not be discharged into a building from the liquid fuel supply system. Liquid-level indicating gauges shall comply with UL 180.
A tank used in connection with any oil burner shall not be equipped with a glass gauge or any gauge that, when broken, will permit the escape of oil from the tank.