// CODE SNIPPET
505.0 Oil-Burning and Other Water Heaters
Jump To Full Code Chapter
505.1 Water Heaters
Water heaters deriving heat from fuels or types of energy other than gas shall comply with the standards referenced in Table 501.1(1), Section 505.3, or Section 505.4. Vents or chimneys for such appliances shall be of approved types. An adequate supply of air for combustion and for adequate ventilation of heater rooms or compartments shall be provided. Each such appliance shall be installed in a location approved by the Authority Having Jurisdiction and local and state fire-prevention agencies.
505.2 Safety Devices
Storage-type water heaters and hot water boilers deriving heat from fuels or types of energy other than gas, shall be provided with, in addition to the primary temperature controls, an over-temperature safety protection device that complies with and is installed in accordance with nationally recognized applicable standards for such devices and a combination temperature and pressure-relief valve.
505.3 Oil-Fired Water Heaters
Oil-fired water heaters shall be installed in accordance with NFPA 31.
505.4 Indirect-Fired Water Heaters
Indirect-fired water heaters shall be in accordance with the applicable sections of the ASME Boiler and Pressure Vessel Code or shall comply with one of the other applicable standards shown in Table 501.1(1). Each water heater shall bear a label in accordance with ASME requirements, or an approved testing agency, certifying and attesting that such an appliance has been tested, inspected and meets the requirements of the applicable standards or code.
505.4.1 Single-Wall Heat Exchanger
An indirect-fired water heater that incorporates a single-wall heat exchanger shall be in accordance with the following requirements:
- The heat transfer medium shall be either potable water or contain fluids recognized as safe by the Food and Drug Administration (FDA) as food grade.
- Bear a label with the word "Caution," followed by the following statements:
- The word "Caution" and the statements in letters shall have an uppercase height of not less than 0.120 of an inch (3.048 mm). The vertical spacing between lines of type shall be not less than 0.046 of an inch (1.168 mm). Lowercase letters shall be compatible with the uppercase letter size specification.
Related Code Sections
505.0 Water Heaters, Oil-Burning and Other Water Heaters
Water heaters deriving heat from fuels or types of energy other than gas shall comply with the standards referenced in Table 501.1(1), Section 505.3 ...
Section 916 Specific Appliances, Fireplaces and Solid Fuel-Burning Equipment, Pool and Spa Heaters
Pool and spa heaters shall be installed in accordance with the manufacturer's instructions. Oil-fired pool and spa heaters shall be tested ...
Section 920 Specific Appliances, Fireplaces and Solid Fuel-Burning Equipment, Unit Heaters
Unit heaters shall be installed in accordance with the listing and the manufacturer's instructions. Oil-fired unit heaters shall be tested ...
509.5.7 Water Heaters, Chimney Serving Appliances Burning Other Fuels
] A single chimney flue serving a listed combination gas- and oil-burning appliance shall be sized in accordance with the appliance ...
509.5.7.3 Water Heaters, Combination Gas- And Oil-Burning Appliances
A single chimney flue serving a listed combination gas- and oil-burning appliance shall be sized in accordance with the appliance manufacturer's ...