// CODE SNIPPET
(1) Number of Disconnecting Means
JUMP TO FULL CODE CHAPTER
- A listed fire pump controller
- A listed fire pump power transfer switch
- A listed combination fire pump controller and power transfer switch
(c) On-Site Standby Generator. Where an on-site standby generator is used to supply a fire pump, an additional disconnecting means and an associated overcurrent protective device(s) shall be permitted.
Related Code Sections
(1) Special Equipment, Number of Disconnecting Means
(a) General . A single disconnecting means and associated overcurrent protective device(s) shall be permitted to be installed between the fire pump ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 695 Fire Pumps > 695.4 Continuity of Power > (B) Connection Through Disconnecting Means and Overcurrent Device > (1) Number of Disconnecting Means
620.55 Special Equipment, Utilization Equipment Disconnecting Means
shall be numbered to correspond to the identifying number of the equipment served. The disconnecting means shall be provided with a sign to identify ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 620 Elevators, Dumbwaiters, Escalators, Moving Walks, Platform Lifts, and Stairway Chairlifts > 620.55 Utilization Equipment Disconnecting Means
(3) Special Occupancies, Separate Feeders to Single Primary Stage Switchboard (Dimmer Bank)
switchboard shall have a permanent and obvious label stating the number and location of disconnecting means. If the disconnecting means are located in more ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 520 Theaters, Audience Areas of Motion Picture and Television Studios, Performance Areas, and Similar Locations > 520.27 Stage Switchboard Feeders > (A) Type of Feeder > (3) Separate Feeders to Single Primary Stage Switchboard (Dimmer Bank)
(C) Special Equipment, Maximum Number of Disconnects
does not limit the number of PV systems connected to a service as permitted in 690.4(D). This requirement allows up to six disconnecting means ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 690 Solar Photovoltaic (PV) Systems > 690.13 Photovoltaic System Disconnecting Means > (C) Maximum Number of Disconnects
430.112 Equipment for General Use, Motors Served by Single Disconnecting Means
Each motor shall be provided with an individual disconnecting means. Exception: A single disconnecting means shall be permitted to serve a group ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 430 Motors, Motor Circuits, and Controllers > 430.112 Motors Served by Single Disconnecting Means