(G) NPLFA Cable Markings
Informational Note: Cable types are listed in descending order of fire performance.
Table 760.176(G) NPLFA Cable Markings
|NPLFP||Non-power-limited fire alarm circuit cable for use in "other space used for environmental air"||760.176(C) and (G)|
|NPLFR||Non-power-limited fire alarm circuit riser cable||760.176(D) and (G)|
|NPLF||Non-power-limited fire alarm circuit cable||760.176(E) and (G)|
Note: Cables identified in 760.176(C), (D), and (E) and meeting the requirements for circuit integrity shall have the additional classification using the suffix "-CI" (for example, NPLFP-CI, NPLFR-CI, and NPLF-CI).