// CODE SNIPPET
(1) Not Less Than 450 mm (18 In.) Above Floor
Related Code Sections
(1) Special Occupancies, Not Less Than 450 mm (18 In.) Above Floor
Aircraft energizers shall be designed and mounted such that all electrical equipment and fixed wiring will be at least 450 mm (18 in.) above floor ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 513 Aircraft Hangars > 513.10 Special Equipment > (C) External Power Sources for Energizing Aircraft > (1) Not Less Than 450 mm (18 In.) Above Floor
Article 450 Equipment for General Use, Transformers and Transformer Vaults (Including Secondary Ties)
not less than the load to be served. (b) Not Interconnected. The loads shall be connected to one or more individual conductors of a paralleled ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 450 Transformers and Transformer Vaults (Including Secondary Ties)
(A) Wiring and Protection, Above Roofs
the voltage between conductors does not exceed 300, a reduction in clearance above only the overhanging portion of the roof to not less than 450 mm ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 225 Outside Branch Circuits and Feeders > 225.19 Clearances From Buildings for Conductors of Not Over 1000 Volts, Nominal > (A) Above Roofs
(4) Wiring and Protection, Other Loads
with taps extending not longer than 450 mm (18 in.) beyond any portion of the lampholder or luminaire A luminaire having tap conductors as provided ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 210 Branch Circuits > 210.19 Conductors — Minimum Ampacity and Size > (A) Branch Circuits Not More Than 600 Volts > (4) Other Loads
188.8.131.52 Electric Elevators,
In elevators where access to the pit is through the lowest landing hoistway door, a stop switch shall be located approximately 450 mm (18 in.) above ...
Safety Code for Elevators and Escalators 2016 of Minnesota > 2 Electric Elevators > 2.2 Pits > 2.2.6 Stop Switch in Pits > 184.108.40.206