Rainwater shall be collected only from above-ground impervious roofing surfaces constructed from approved materials. Collection of water from vehicular parking or pedestrian walkway surfaces shall be prohibited except where the water is used exclusively for landscape irrigation. Overflow and bleed-off pipes from roof-mounted appliances including, but not limited to, evaporative coolers, water heaters and solar water heaters shall not discharge onto rainwater collection surfaces.
Downspouts and leaders shall be connected to a roof washer and shall be equipped with a debris excluder or equivalent device to prevent the contamination of collected rainwater with leaves, sticks, pine needles and similar material. Debris excluders and equivalent devices shall be self-cleaning.
An amount of rainwater shall be diverted at the beginning of each rain event, and not allowed to enter the storage tank, to wash accumulated debris from the collection surface. The amount of rainfall to be diverted shall be field adjustable as necessary to minimize storage tank water contamination. The roof washer shall not rely on manually operated valves or devices, and shall operate automatically. Diverted rainwater shall not be drained to the roof surface, and shall be discharged in a manner consistent with the storm water runoff requirements of the jurisdiction. Roof washers shall be accessible for maintenance and service.
Gutters and downspouts shall be constructed of materials that are compatible with the collection surface and the rainwater quality for the desired end use. Joints shall be watertight.
Roof gutters, leaders and rainwater collection piping shall slope continuously toward collection inlets and shall be free of leaks. Gutters and downspouts shall have a slope of not less than 1/8 inch per foot (10.4 mm/m) along their entire length. Gutters and downspouts shall be installed so that water does not pool at any point.
Cleanouts shall be provided in the water conveyance system to allow access to filters, flushes, pipes and downspouts.
Water drained from the roof washer or debris excluder shall not be drained to the sanitary sewer. Such water shall be diverted from the storage tank and shall discharge to a location that will not cause erosion or damage to property. Roof washers and debris excluders shall be provided with an automatic means of self-draining between rain events and shall not drain onto roof surfaces.
Rainwater collection and conveyance systems shall utilize drainage piping approved for use within plumbing drainage systems to collect and convey captured rainwater. Vent piping approved for use within plumbing venting systems shall be utilized for vents within the rainwater system. Collection and vent piping materials shall comply with Section P3002.
Collection piping conveying captured rainwater shall be installed in accordance with Section P3005.3.
Collection piping conveying captured rainwater shall utilize joints approved for use with the distribution piping and appropriate for the intended applications as specified in Section P3003.
Collection piping conveying captured rainwater shall be sized in accordance with drainage-sizing requirements specified in Section P3005.4.
Collected rainwater shall be filtered as required for the intended end use. Filters shall be accessible for inspection and maintenance. Filters shall utilize a pressure gauge or other approved method to provide indication when a filter requires servicing or replacement. Filters shall be installed with shutoff valves installed immediately upstream and downstream to allow for isolation during maintenance.
Where the intended application for rainwater requires disinfection or other treatment or both, it shall be disinfected as needed to ensure that the required water quality is delivered at the point of use.
Storage tanks shall be located with a minimum horizontal distance between various elements as indicated in Table P2912.10.1.
TABLE P2912.10.1 LOCATION OF RAINWATER STORAGE TANKS
TABLE P2912.10.1 LOCATION OF RAINWATER STORAGE TANKS
|ELEMENT|| MINIMUM HORIZONTAL DISTANCE |
FROM STORAGE TANK
|Critical root zone (CRZ) of protected trees||2|
|Lot line adjoining private lots||5|
For SI: 1 foot = 304.8 mm
Storage tank inlets shall be designed to introduce collected rainwater into the tank with minimum turbulence, and shall be located and designed to avoid agitating the contents of the storage tank.
Outlets shall be located not less than 4 inches (102 mm) above the bottom of the storage tank and shall not skim water from the surface.
A means shall be provided to divert storage tank influent to allow for maintenance and repair of the storage tank system.
Where the water pressure supplied by the pumping system exceeds 80 psi (552 kPa) static, a pressure-reducing valve shall be installed to reduce the pressure in the rainwater distribution system piping to 80 psi (552 kPa) static or less. Pressure-reducing valves shall be specified and installed in accordance with Section P2903.3.1.
Distribution piping shall conform to the standards and requirements specified in Section P2906 for nonpotable water.
Distribution piping systems shall be designed and sized in accordance with the Section P2903 for the intended application.
Nonpotable rainwater distribution piping labeling and marking shall comply with Section P2901.2.
Roof gutters shall be inspected to verify that the installation and slope is in accordance with Section P2912.5.1. Gutters shall be tested by pouring not less than one gallon of water (3.8 L) into the end of the gutter opposite the collection point. The gutter being tested shall not leak and shall not retain standing water.
Roofwashers shall be tested by introducing water into the gutters. Proper diversion of the first quantity of water in accordance with the requirements of Section P2912.4 shall be verified.
The testing of makeup water supply piping and distribution piping shall be conducted in accordance with Section P2503.7.
This section has been amended at the state or city level.
The testing of backflow preventers and backwater valves shall be conducted in accordance with Section P2503.8.
The quality of the water for the intended application shall be verified at the point of use in accordance with the requirements of the jurisdiction.
A detailed operations and maintenance manual shall be supplied in hard-copy form for each system.
The manual shall include a detailed system schematic, the location of system components and a list of system components that includes the manufacturers and model numbers of the components.
The manual shall provide a maintenance schedule and procedures for system components requiring periodic maintenance. Consumable parts, including filters, shall be noted along with part numbers.
The manual shall include system startup and shutdown procedures, and detailed operating procedures.