// CODE SNIPPET
250.116 Nonelectrical Equipment
JUMP TO FULL CODE CHAPTER
The metal parts of the following nonelectrical equipment described in this section shall be connected to the equipment grounding conductor:
- Frames and tracks of electrically operated cranes and hoists
- Frames of nonelectrically driven elevator cars to which electrical conductors are attached
- Hand-operated metal shifting ropes or cables of electric elevators
Informational Note: Where extensive metal in or on buildings or structures may become energized and is subject to personal contact, adequate bonding and grounding will provide additional safety.