// CODE SNIPPET
607.8 Noncombustible Receptacle
JUMP TO FULL CODE CHAPTER
The receptacle shall be securely suspended from the floor members and shall be not more than 18 inches (457 mm) below the floor opening.
The area of the receptacle shall extend 3 inches (76 mm) beyond the opening on all sides.
The perimeter of the receptacle shall have a vertical lip not less than 1 inch (25.4 mm) high at the open sides where it is at the level of the bottom of the joists, or 3 inches (76 mm) high where the receptacle is suspended.