// CODE SNIPPET
508.5.2 Noncanopy-Type Hoods
JUMP TO FULL CODE CHAPTER
In addition to other requirements for hoods specified in this section, the volume of air exhausting through a noncanopy-type hood to the duct system shall be not less than 300 cubic feet per minute per lineal foot [(ft3/min)/ft)] [0.464 (m3/s)/m] of cooking equipment. Listed noncanopy exhaust hoods and filters shall be sized and installed in accordance with the terms of their listing and the manufacturer's installation instructions.
Related Code Sections
508.5.2 Exhaust Systems, Noncanopy-Type Hoods
Noncanopy-type commercial cooking hoods shall be installed and sized in accordance with the manufacturer's installation instructions, and Section ...
Uniform Mechanical Code 2018 of Nevada > 5 Exhaust Systems > 508.0 Type I Hoods > 508.5 Hood Size > 508.5.2 Noncanopy-Type Hoods
931.5.2 Installation of Specific Appliances, Hoods
A canopy-type hood shall be installed directly above each kiln. The face opening area of the hood shall be equal to or greater than the top ...
Uniform Mechanical Code 2018 of Nevada > 9 Installation of Specific Appliances > 931.0 Small Ceramic Kilns > 931.5 Installations Inside Buildings > 931.5.2 Hoods
(4) Equipment for General Use, Range Hoods
Range hoods shall be permitted to be cord-and-plug-connected with a flexible cord identified as suitable for use on range hoods in the installation ...
National Electrical Code 2017 of Nevada > 4 Equipment for General Use > 422 Appliances > 422.16 Flexible Cords > (B) Specific Appliances > (4) Range Hoods
508.5.1.1 Exhaust Systems, Capacity of Hoods
Canopy-type commercial cooking hoods shall exhaust through the hood with a quantity of air not less than determined by the application in accordance ...
Uniform Mechanical Code 2018 of Nevada > 5 Exhaust Systems > 508.0 Type I Hoods > 508.5 Hood Size > 508.5.1 Canopy Size and Location > 508.5.1.1 Capacity of Hoods
508.2.1 Exhaust Systems, Listed Ultraviolet Hoods
Listed ultraviolet hoods shall be installed and maintained in accordance with the terms of their listing and the manufacturer's installation ...
Uniform Mechanical Code 2018 of Nevada > 5 Exhaust Systems > 508.0 Type I Hoods > 508.2 Listed Type I Hood Assemblies > 508.2.1 Listed Ultraviolet Hoods