// CODE SNIPPET
803.1 Neutralizing Device Required for Corrosive Wastes
JUMP TO FULL CODE CHAPTER
Corrosive liquids, spent acids or other harmful chemicals that destroy or injure a drain, sewer, soil or waste pipe, or create noxious or toxic fumes or interfere with sewage treatment processes shall not be discharged into the plumbing system without being thoroughly diluted, neutralized or treated by passing through an approved dilution or neutralizing device. Such devices shall be automatically provided with a sufficient supply of diluting water or neutralizing medium so as to make the contents noninjurious before discharge into the drainage system. The nature of the corrosive or harmful waste and the method of its treatment or dilution shall be approved prior to installation.
Related Code Sections
803.1 Indirect/Special Waste, Neutralizing Device Required for Corrosive Wastes
Corrosive liquids, spent acids or other harmful chemicals that destroy or injure a drain, sewer , soil or waste pipe, or create noxious or toxic ...
Plumbing Code 2018 of Kansas > 8 Indirect/Special Waste > 803 Special Wastes > 803.1 Neutralizing Device Required for Corrosive Wastes
801.1 Indirect/Special Waste, Scope
devices for corrosive wastes ...
1009.4 Change of Occupancy, Chemical Wastes
, the waste shall be neutralized prior to entering the drainage system, or the piping shall be changed to a compatible material. Chemical waste shall ...
Existing Building Code 2018 of Kansas > 10 Change of Occupancy > 1009 Plumbing > 1009.4 Chemical Wastes
(B) Equipment for General Use, Bonded Neutral Generators
)(3) for GFCI requirements for 15-kW or smaller portable generators used for temporary electric power and lighting. Exception to (A) and (B): If ...
National Electrical Code 2017 of Kansas > 4 Equipment for General Use > 445 Generators > 445.20 Ground-Fault Circuit-Interrupter Protection for Receptacles on 15-kW or Smaller Portable Generators > (B) Bonded Neutral Generators
368.258 Wiring Methods and Materials, Neutral Conductor
Neutral bus, where required, shall be sized to carry all neutral load current, including harmonic currents, and shall have adequate momentary ...
National Electrical Code 2017 of Kansas > 3 Wiring Methods and Materials > 368 Busways > 368.258 Neutral Conductor