// CODE SNIPPET
(D) Multiwire Circuits, Not Permitted
Related Code Sections
(D) Special Equipment, Multiwire Circuits, Not Permitted
An individual office furnishing or groups of interconnected office furnishings shall not contain multiwire circuits. Informational Note: See 210.4 ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 605 Office Furnishings > 605.9 Freestanding-Type Office Furnishings, Cord-And Plug-Connected > (D) Multiwire Circuits, Not Permitted
(1) Wiring and Protection, Multiwire Branch Circuits
Individual single-pole circuit breakers, with identified handle ties, shall be permitted as the protection for each ungrounded conductor of multiwire ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 240 Overcurrent Protection > 240.15 Ungrounded Conductors > (B) Circuit Breaker as Overcurrent Device > (1) Multiwire Branch Circuits
210.4 Wiring and Protection, Multiwire Branch Circuits
Branch circuits recognized by this article shall be permitted as multiwire circuits. A multiwire circuit shall be permitted to be considered ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 210 Branch Circuits > 210.4 Multiwire Branch Circuits
(B) Wiring Methods and Materials, Multiwire Branch Circuits
Where connected to a multiwire branch circuit, the disconnecting means shall simultaneously disconnect all the supply conductors, including ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 393 Low-Voltage Suspended Ceiling Power Distribution Systems > 393.21 Disconnecting Means > (B) Multiwire Branch Circuits
(2) Equipment for General Use, Multiwire Branch Circuits
When connected to multiwire branch circuits, the disconnecting means shall simultaneously break all the supply conductors to the ballast, including ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 410 Luminaires, Lampholders, and Lamps > 410.130 General > (G) Disconnecting Means > (2) Multiwire Branch Circuits