// CODE SNIPPET
C101.10.1 Multiple Collection Reservoirs Required
JUMP TO FULL CODE CHAPTER
Related Code Sections
C101.10.1 Water Recycling Systems, Multiple Collection Reservoirs Required
Separate collection tanks or compartments shall be provided for influent wastewater and rainwater. Where multiple collection reservoirs are provided ...
NYC Plumbing Code 2014 > C Water Recycling Systems > C101 General > C101.10 Collection Reservoir > C101.10.1 Multiple Collection Reservoirs Required
C101.4 Water Conservation Systems, Reservoir
Water captured for recycling purposes shall be collected in an approved reservoir constructed of durable, nonabsorbent and corrosion-resistant ...
NYC Plumbing Code 2008 > C Water Conservation Systems > C101 Water Recycling Systems > C101.4 Reservoir
1305.9.3 Fuel-Oil Piping and Storage, Horizontal Offsets
at a supervising station. The wiring shall comply with the New York City Electrical Code . Exception: A leak collection reservoir is not required where double ...
NYC Mechanical Code 2022 > 13 Fuel-Oil Piping and Storage > 1305 Fuel-Oil System Installation > 1305.9 Supplemental Requirements for Piping From Transfer Pumps to Appliances or Storage Tanks Above Lowest Floor > 1305.9.3 Horizontal Offsets
3.5.2 Definitions, Air Reservoir
A chamber that can store air at the same pressure that is in the wet pipe system piping ...
Standard for the Installation of Sprinkler Systems 2016 of New York City > 3 Definitions > 3.5* System Component Definitions > 3.5.2 Air Reservoir
3.3.8* Definitions, Draft Curtain
A continuous material protruding downward from the ceiling to create a reservoir for collecting smoke and heat ...
Standard for the Installation of Sprinkler Systems 2016 of New York City > 3 Definitions > 3.3 General Definitions > 3.3.8* Draft Curtain