(3) Multiple Buildings or Structures Supplied by a Feeder(s) or Branch Circuit(s)
- Building or structure disconnecting means enclosure where located at the building or structure
- Equipment grounding conductor run with the supply conductors
- One or more grounding electrodes used
The bonding jumper(s) shall be sized in accordance with Table 250.102(C)(1), based on the size of the feeder or branch-circuit conductors that supply the building or structure. The bonding jumper shall not be required to be larger than the largest ungrounded feeder or branch-circuit conductor supplying the building or structure.