A126.96.36.199 Multilevel Occupant Sensor
Multilevel occupant sensors shall have an automatic OFF function that turns off all the lights and either an automatic or a manually controlled ON function capable of meeting all the multilevel and uniformity requirements of Section A188.8.131.52 for the controlled lighting. The first stage shall be capable of activating between 30—70 percent of the lighting power in a room either through an automatic or manual action and may be a switching or dimming system. After that event occurs the device shall be capable of all of the following actions when manually called to do so by the occupant:
- Activating the alternate set of lights.
- Activating 100 percent of the lighting power.
- Deactivating all lights.