// CODE SNIPPET
(3) Multiconductor Jacketed Cables
JUMP TO FULL CODE CHAPTER
Where part of a listed PV assembly, multiconductor jacketed cables shall be installed in accordance with the included instructions. Where not part of a listed assembly, or where not otherwise covered in this Code, multiconductor jacketed cables, including DG cable, shall be installed in accordance with the product listing and shall be permitted in PV systems. These cables shall be installed in accordance with the following:
- In raceways, where on or in buildings other than rooftops
- Where not in raceways, in accordance with the following:
- Marked sunlight resistant in exposed outdoor locations
- Protected or guarded, where subject to physical damage
- Closely follow the surface of support structures
- Secured at intervals not exceeding 1.8 m (6 ft)
- Secured within 600 mm (24 in.) of mating connectors or entering enclosures
- Marked direct burial, where buried in the earth
Related Code Sections
(3) Special Equipment, Multiconductor Jacketed Cables
Where part of a listed PV assembly, multiconductor jacketed cables shall be installed in accordance with the included instructions. Where not part ...
National Electrical Code 2020 of Minnesota > 6 Special Equipment > 690 Solar Photovoltaic (PV) Systems > 690.31 Wiring Methods > (C) Cables > (3) Multiconductor Jacketed Cables
522.21 Special Occupancies, Conductor Sizing
and jacketed multiconductor cable within an enclosure or operator station. Conductors in a non-jacketed multiconductor cable, such as ribbon cable, shall ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 522 Control Systems for Permanent Amusement Attractions > 522.21 Conductor Sizing
(B) General, Equipment Grounding Conductors
An equipment grounding conductor shall be run with circuit conductors inside the metal raceway or inside the multiconductor cable jacket. The ...
National Electrical Code 2020 of Minnesota > 1 General > 110 Requirements for Electrical Installations > 110.54 Bonding and Equipment Grounding Conductors > (B) Equipment Grounding Conductors
(E) Wiring and Protection, Separately Bushed Openings
Service heads shall have conductors of different potential brought out through separately bushed openings. Exception: For jacketed multiconductor ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 230 Services > 230.54 Overhead Service Locations > (E) Separately Bushed Openings
337.115 Wiring Methods and Materials, Jacket
Single conductor cables and multiconductor cables shall have an overall nonmetallic jacket that is impervious to moisture, corrosion resistant ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 337 Type P Cable > 337.115 Jacket