// CODE SNIPPET
C405.2.2.3.3 Multi-Level Lighting Controls
JUMP TO FULL CODE CHAPTER
Where multi-level lighting controls are required by this code, the general lighting in the daylight zone shall be separately controlled by at least one multi-level lighting control that reduces the lighting power in response to daylight available in the space. Where the daylit illuminance in the space is greater than the rated illuminance of the general lighting of daylight zones, the general lighting shall be automatically controlled so that its power draw is no greater than 35 percent of its rated power. The multi-level lighting control shall be located so that calibration and set point adjustment controls are readily accessible and separate from the light sensor.
Related Code Sections
C405.2.2.3.3 [CE] Commercial Energy Efficiency, Multi-Level Lighting Controls
Where multi-level lighting controls are required by this code, the general lighting in the daylight zone shall be separately controlled by at least ...
Energy Conservation Code 2012 of Nevada > 4 [CE] Commercial Energy Efficiency > C405 Electrical Power and Lighting Systems (Mandatory) > C405.2 Lighting Controls (Mandatory) > C405.2.2 Additional Lighting Controls > C405.2.2.3 Daylight Zone Control > C405.2.2.3.3 Multi-Level Lighting Controls
504.8.2 General Site and Building Elements, Lighting Controls
If provided, occupancysensing automatic controls shall activate the stairway lighting so the illuminance level required by Section 504.8.1 ...
Accessible and Usable Buildings and Facilities 2009 of Nevada > 5 General Site and Building Elements > 504 Stairways > 504.8 Lighting > 504.8.2 Lighting Controls
*1.3-3.2 Site, Lighting
Site lighting shall be provided for the patient path of travel. A1.3-3.2 Site lighting. Lighting controls should permit zoned operation, allowing ...
Guidelines for Design and Construction of Outpatient Facilities 2018 of Nevada > 1.3 Site > *1.3-3 Site Features > *1.3-3.2 Lighting
*1.3-3.2 Site, Lighting
Site lighting shall be provided on roads, parking lots, and pedestrian walkways. A1.3-3.2 Site lighting. Lighting controls should permit ...
Guidelines for Design and Construction of Hospitals 2018 of Nevada > 1.3 Site > 1.3-3 Site Features > *1.3-3.2 Lighting
Section E3903 Power and Lighting Distribution, Lighting Outlets
to control the lighting outlets where the stairway between floor levels has six or more risers. Exception: In hallways, stairways, and at outdoor egress ...